Table of Contents

## What is XR ratio of transformer?

All Answers (3) Hitachi, Ltd. The XR Ratio of a transformer is the imaginery portion (j), of the impedance divided by the Real part. In your case considerations are: are you trying to calculate it as a network sequence or separate line entities, this makes a difference of what will result.

## What is the significance of x r ratio?

Why is the X/R ratio important? Its importance is that it affects the level of short circuit current a circuit breaker is required to interrupt. When a short circuit occurs, the rms value of the symmetrical fault current is determined by the system source voltage and the total system impedance to the point of fault.

## What are X R ratios?

The X/R ratio affects the dc component, and therefore, also the total current. The higher the X/R ratio of a circuit, the longer the dc component will take to decay (longer time constant). To illustrate, two circuits are shown in Figure 1.

## What is electrical XR?

As an extended reality (XR) electrical engineer, you will design and develop systems and components. You could be involved in projects from as early as the concept stage, through to implementation and testing.

## What is Z in transformer?

The percentage impedance of a transformer (Z%) is the voltage drop on full load due to the winding resistance and leakage reactance expressed as a percentage of the rated voltage. The ratio of voltage applied to circulate full load current to the primary voltage is the percentage impedance of the transformer.

## What is the short circuit ratio of transformer?

Short circuit ratio or SCR is a measure of the stability of an electromechanical generator. It is the ratio of field current required to produce rated armature voltage at open circuit to the field current required to produce the rated armature current at short circuit.

## What is XR ratio of transmission line?

In Transmission Lines the Deq which is the Geometric Mean distance among conductors is very larger than overhead distribution lines. So the X/R ratio in transmission lines is larger than distribution lines. In underground distribution networks (cables) the X/R ratio is very small and may be smaller than 1.

## What is asymmetrical fault current?

Asymmetrical short-circuit current: A fault current whose waveform is asymmetrical to the zero axis. The peak positive current at any of the waveform loops will be greater than 1.414 times the rms symmetrical current. In other words, the positive peak current has the same value as the negative peak current.

## What is short circuit power factor?

Power factor (PF) is sometimes specified instead of X/R. This must be the short circuit power factor. Power factor is defined as the cosine of the angle between voltage and current. X/R is the tangent of this same angle. X/R can be found from power factor by taking the tangent of the inverse cosine of the power factor.

## What is short circuit current ratio?

## When do you use the X / are ratio?

For the case where the X/R ratios give angles that are close, there is little difference between the two methods such as our case where we have an X/R of 15 which is 86.1859° and 7 which is 81.8699°. In most cases, however, there is usually a greater difference in angles such as when factoring in smaller transformers and low voltage conductor.

## What does the X / are ratio of a circuit mean?

This indicates the time the asymmetrical fault current decays to become symmetrical. As shown in Figure 3, the DC component for the circuit with X/R ratio of 50 is more prolonged: 30 cycles for X/R ratio of 50 as compared to 3 cycles in the circuit with X/R ratio of 5. The higher the X/R ratio, the slower the DC component decays.

## What should the X / are ratio be for 220 kV?

X/R Ratio The range of X/R values for typical voltage class (Canadian) are as follows: 735 kV, 18.9-20.4; 500 kV, 13.6-16.5; 220 kV, 2-25; 110 kV, 3-26. The X/R value decreases with separation of the fault point from the source and can be substantially decreased by the fault resistance.

## What should the X / are ratio of a lvcb be?

The LVCB was tested at X/R of 6.6 (0.15 power factor). This test X/R ratio is not provided on the circuit breaker nameplate. (For reference, high voltage circuit breakers are typically tested at X/R ratio of 17. Special purpose generator circuit breakers are typically tested at X/R ratio of 50.)